Int. J. Metrol. Qual. Eng.
Volume 10, 2019
|Number of page(s)||8|
|Published online||20 September 2019|
Supercapacitor based PV measurement technique − quality assessment with poly-Si PV modules at IIEST, Kolkata
Electrical Engineering, Indian Institute of Engineering Science and Technology, Shibpur, Howrah, India
2 Electronics and Telecommunication Engineering, Indian Institute of Engineering Science and Technology, Shibpur, Howrah, India
* Corresponding author: firstname.lastname@example.org
Accepted: 4 July 2019
Supercapacitors have been used for the first time as load to PV cell/modules for characterizing their behavior. In this paper, a novel and essentially simple design of a V–I plotter is attempted with a bank of super capacitors (SC) as the load to the PV modules of varying capacities. The distinct advantages of the SC's over the erstwhile capacitors have been comparatively experimented. Finally, an elaborate regression analysis (RA) of principal electrical parameters have yielded consistently high values exceeding 0.993 experimental evaluation of quality parameters like fill-factor (FF) and performance ratio (PR) have yielded a range of 70–79% while PR values frequently ranges from 90% to 99%. Suitability of poly-Si PV modules at the level of PV panel configurations have been ascertained through experimental estimate of series and parallel relative power loss (RPL) values. Typical values below 2% obtained for widely varying climatic level is also a quality indicator for the new metrology in question. Such a prototype I–V plotter is expected to be duly considered for commercial testing applications in PV industries.
Key words: SPS / RES / PV power plants / supercapacitors / PV generators / performance ratio
© S. Basu Pal et al., published by EDP Sciences, 2019
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
The rapid penetration of the solar photovoltaic systems (SPS) into the electrical networks at different voltage levels is now an accepted global phenomenon. Penetration of renewable energy sources (RES) into the average European grid is expected to cross 30% by the end of 2022, 12% of such shares being specifically contributed from photovoltaics . India has already embarked on a policy  of delivering at least 20% of grid-power through renewable energy sources (RES) by 2020. Accordingly, massive efforts are currently being undertaken in India for large-scale installations of PV power plants of megawatts capacity. This calls for an appropriate and smart metrological procedure for selecting the PV modules, acting as the building blocks to the high capacity PV arrays .
The aforesaid situation is responsible for expanding the role of an online, accurate and inexpensive V–I plotter outside the academic laboratories also. Thus, the next section is essentially devoted to a review of the existing metrological approaches practiced in PV engineering for establishing the specific merits of the supercapacitor (SC) based method introduced by the authors. Here, supercapacitors have been used in the area of PV metrology for the first time as the load to the PV generators [3–5].
The conventional analog method of determination of the V–I characteristic of a solar module involves a variable resistance used as the load. A typical V–I characteristics of any PV module is shown in Figure 1, where there are two extremities − the short circuit current point (I sc,0) and open circuit voltage point (0, V oc). The standard electrical parameters of interest in any V–I plot are the following: short circuit current (I sc), open circuit voltage (V oc), peak power current point (Im ), peak power voltage point (Vm ), maximum power point (Pm ).
By varying the resistive load, the above co-ordinates can be approached but not reached. Further, this manual process consumes sufficient time leading to undesired heating of all the p-n junctions of a PV module.
To minimize the human intervention and to characterize the PV module faster and accurately researchers started to use electronic loads instead of resistive loads. Linear MOSFET can be used as an electronic load to test the PV panel. Advantage of the electronic load is the fast variation (scanning) of the equivalent load resistance. Various commercial grade systems for testing PV panels under field conditions are available but they are computer controlled and are very expensive. A MOSFET based electronic load circuit was introduced by Kuai et al. . Recently Sahbel et al. designed a simple electronic circuit for testing the photovoltaic (PV) modules by tracing their I–V characteristics . However, such methods are constrained by a requirement of an expensive test setup primarily suited to the laboratory measurement conditions only. In the next phase of development, researchers developed capacitor charging with the aid of open circuit voltage. Such an effort by Mahmoud  has used capacitors as the load to PV Generators. But, such reports contain a detailed transient analysis, which leads to the estimate of I–V plotting time based on open circuit voltage (V oc) and short circuit current (I sc) only. Also, such reports do not contain real traces of I–V characteristics of PV generators. Further, this method calls for a high precision matching DAS, rendering the plotter higher in capital cost, although other researchers like Erkaya et al. and Spertino et al. [9,10] have in the recent past used capacitive load. Very recently Zhikong et al.  proposed new capacitor-based design and implementation of an I–V characteristics tester. The setup is quite efficient to characterize PV arrays quickly. But this type of tracer is not able to characterize a single PV cell/module/panel. But neither of these curve tracers provides an assessment of the V–I plotting time and effective means to control the same.
On the above backdrop, authors of this paper have introduced a new technique where Supercapacitors have replaced the capacitors with the plotting time modeled out as a function of four basic electrical parameters (I sc, V oc, Im , Vm ) along with the effective series resistance (ESR) value of the SC bank. This is reported in details in an earlier publication .
On the above backdrop, authors of this paper have introduced a new technique where supercapacitors have replaced the capacitors with the plotting time modeled out as a function of four basic electrical parameters
short circuit current (I sc),
open circuit voltage (V oc),
maximum current at maximum power point (Im ) and
maximum voltage at maximum power point (Vm ) along with the effective series resistance (ESR) value of the SC bank. This is reported in details in an earlier publication .
Photovoltaic module voltage–current characteristics.
In this work, supercapacitors have been used as a measuring element rather than a storage device. In this case, note worthy advantages of SC's are:
Desirable control of the plotting time when the voltage of SC approaches V OC.
The thermal management of the Supercapacitor bank is possible without the use of any kind of heatsink, as the heat dissipation is not expected to cross a level of few watts, prevailing for only 10–15 s. This is clearly evidenced from Table 1.
A high Coulombic efficiency exceeding 99%, leading to fast sweep between V = 0 to V = V oc.
A wide range of capacitances available with low ESR values (within few milliohms) .
A voltage range compatible with the open circuit voltages of standard PV modules and panels.
To establish the superiority of supercapacitor-based loading method a comparative table for SC based and capacitor-based methods with respect to accuracy in estimation of curve tracing time is to be shown in Table 1.
Moreover, an experimental estimation of heat dissipation for 100 Wp PV modules using supercapacitors is shown in Table 2. The heat dissipation values in the last column have been estimated by considering individual ESR value of the supercapacitors to be 0.02Ω and the total ESR value of the Supercapacitor bank is 0.12Ω (optimum combination of six SC's in series). Same experiments were also carried out using capacitances of rating 10,000 μF, 25 V with 1 ohm ESR value and the charging currents utilized to estimate the different heat dissipation amounts as shown in Table 3.
It is clearly seen from the above two tables that capacitor-based characterization calls for a separate heat sink to dissipate the excessive heat generated. Further disadvantage of using the capacitor as the load to the PV generator requires a higher volume, which also makes some capacitor-based plotters inconvenient for transportation.
Estimate of curve tracing time (for 10Wp, 74Wp and 100Wp poly-Si PV module).
Heat dissipation when 100 Wp PV modules use supercapacitor loading.
Heat dissipation for 100 Wp PV Modules using capacitor loading.
Figure 2 represents typically a block diagram of the testing scheme used by the authors.
The solar PV modules or panels (combination of PV modules) have been fitted into the steel structure and placed at the roof-top. Voltage and current inputs are via VC (voltage channel) and CC (current channel) respectively. For accurate insolation sensing a 3 Wp c-Si solar PV panel has been placed and considered as the reference module. The module back surface temperature is measured using the resistance temperature detector (RTD) cables and this value transferred to the cell temperature by using the known standard relation . The solar PV modules are Polycrystalline type in the range of 10 Wp to 320 Wp. The actual measurement setup is shown in Figure 3. The data acquisition system (DAS) is being made operational on an embedded platform (dsPIC30F4013) making the instrument light-weight and portable. The graphical-LCD (GLCD) display is attached with the measurement setup.
Functional blocks of the testing setup.
Components of author V–I measurement setup.
The task of choosing the elements of the SC bank was performed with initial priority on low ESR  values. The SC banks were configured in two steps:
In the 1st phase, the PV Module's capacity is considered between 10 Wp to 100 Wp. Since the V oc of the 10 watts to 100 Wp PV modules lie between 21 V and 25 V levels, six numbers of series connected 1F, 5.5 V supercapacitors with ESR values (0.022 ohms) were chosen. For the first case, the simple Kamcap supercapacitors have been used, where the equivalent capacitance of the SC Bank = 1/6 = 0.166 F (seen from Fig. 3).
In the second stage, the largest capacity building block in Indian PV arrays is considered. Since the V OC of a 300 Wp PV module is 48 V, lowest ESR values (0.022Ω), supercapacitor bank has been constituted with nine numbers of 7.5F, 5.5 V supercapacitors. A series configuration constitutes an equivalent capacitance value 0.83 F (7.5/9).
It may be mentioned at the outset that Poly-Si PV modules technology currently enjoys the largest share of Indian PV market. Accordingly, authors group has planned the entire schedule of measurement with a leading PV industry in Kolkata. Analysing the aforesaid set of results, a no. of essential figures of merit transpires with a reasonable degree of consistency. Following figures of merit has been envisaged.
Regression analysis  was done for I sc, Im and Pm of PV modules with changing insolation levels. Figure 4 shows values of regression co-efficient (R 2) consistently above 0.95 was obtained for 74 W, 100 W, 320 W poly-Si modules.
Linearity check for the solar PV parameters against insolation variation.
It is the ratio of area covered by Im –Vm rectangle with area covered by I sc–V oc which is given in equation (1) using standard symbols.(1)
Fill factor is an intrinsic property of any PV generator and usually from 0.6 to 0.85 for good quality PV generators. The FF variations with varying insolations and temperature are shown in Figures 5–7. However, in real test conditions FF values lies in the range of 0.7 to 0.8.
FF and PR variation with varying insolation for 74 Wp PV modules.
FF and PR variation with varying insolation for 100 Wp PV modules.
FF and PR variation with varying insolation for 320 Wp PV modules.
The PR is stated as the ratio of the actual and theoretical energy outputs of the PV plant/PV module . Mathematically performance ratio is represented as(2)where, mPMPP, measured power in NON-STC condition; PSTC, measured power in STC conditions; GPOA, insolation actually incident on the plane of array.
It can be observed from the set of I–V characteristics presented in Figure 8 that the curves are all having a smooth trace, where the detection of the maximum power point occurs in a unique fashion for all the curves. Further, no kink/noise level is seen around the maximum power point zone. Uncertainty in determination of maximum power point is thereby eliminated.
V–I characteristics of different wattages poly-Si PV modules across three different seasons.
In line with the classical way of understanding the reproducibility of measurements, in case of PV metrology, the same has to be assessed through the infirmity of quality of the PV performance parameter obtained under naturally varying environmental conditions. Figures 5–7 projects the two essential PV quality parameter FF and PR against naturally varying levels of climatic condition over a full day. Such an exercise for a particular PV module capacity has been repeated for a set of chosen PV building blocks − 74 Wp, 100 Wp, and 320 Wp modules. Error-free measurements obtained under various combinations of insolations and temperatures have been projected in Figure 8 (4 × 3 matrix), where four selected capacity of PV module has been characterized in three different seasons of the year. Thus result gives adequate confidence in the “Reproducibility of the measurements” can be instilled.
Non-identical current-voltage characteristics of PV modules give rise to power loss when modules are connected in series or in the parallel configuration. Such losses are called Mismatch loss. Mismatch losses normally arise due to relative power loss (RPL) or in the form of shading loss. The shading loss is neglected easily by choosing the appropriate PV installation site. RPL loss is the total output power of Series connection or Parallel connection of PV modules will be less than the sum of the total power output of PV modules as if they are acting individually. Table 4 shows the RPL measurement for 50 Wp and 100 Wp Poly-Si PV modules in Eastern Indian Climatic Zones. In fact, the quality of measurement so proposed by the authors' metrological approach has been reaffirmed by checking the outdoor performance of small poly-Si PV panels constituted in series and parallel configurations.
RPL measurement for 50 Wp and 100 Wp poly-Si modules.
It is to be noted that the PV Modules experimented upon are all Poly-Si PV modules as such modules are the predominant ones in the current Indian market. The basic building blocks (PV modules) chosen for the purpose of experimentation with the new metrological procedure are 74 Wp, 100 Wp, and 320 Wp poly-Si PV modules.
It is seen from Figure 4 that, consistently high values of R 2 (above 0.98) are found with respect to regression analysis of I sc, Im , Pm of the chosen modules.
Estimated FF values for the aforesaid modules are in the range of 70% to 79%.
The PR values of the building blocks range typically from 90 to 99% for varying levels of insolations.
Finally, RPL values for 50 pW and 100 pW PV panels are typically less than 2.5% and 1.5% for series and the parallel respectively string of PV modules corresponding to insolation above 300 W/m2.
Experimental evidence (a) to (d) is a strong indicator of the inherent quality of the new metrology based on supercapacitors. Field trials with Vikram Solar PV modules are in progress for finalizing an appropriate commercial version of the prototype I–V plotter.
- A. Hsu, Carlin Rosengartin, A. Wein Furter, Y. Xie, Renewable Energy and Energy Efficiency in Developing countries: Contribution to Reducing Global emission, United Nations Environment Programme, Third Report, 2017 [Google Scholar]
- The Jawaharlal Nehru National Solar Mission (National Solar Mission), Launched by MNNRES, Govt of India, 2011 [Google Scholar]
- S. Basu Pal, T. Belel, K. Das (Bhattacharya), D. Mukherjee, A Simple cost Effective method of Characterizing PV Cell/Modules using Supercapacitor, in WCPEC6-November-2014, Kyoto, Japan, 2014 [Google Scholar]
- S. Basu Pal, K. Das (Bhattacharya), D. Mukherjee, D. Paul, Electrical characterization of PV modules employing supercapactors − a scalable method for field metrology, in International Conference on Renewable Energies and Power Quality(ICREPQ), Spain, 2017 [Google Scholar]
- S. Basu Pal, K. Das (Bhattacharya), D. Mukherjee, D. Paul, Estimating of curve tracing time in supercapacitor based PV characterization, J. Inst. Eng. (India) Ser. B 385-391 (2017) [Google Scholar]
- Y. Kuai, S. Yuvarajan, An electronic load for testing photovoltaic panels, J. Power Sources 154 , 308–313 (2005) [Google Scholar]
- A. Sahbela, N. Hassan, M.M. Abdelhameed, A. Zekry, Experimental performance characterization of photovoltaic modules using DAQ, Energy Proc. 36 , 323–332 (2013) [CrossRef] [Google Scholar]
- M.M. Mahmoud, Transient analysis of a PV power generator charging a capacitor for measurement of the I-V characteristics, Renew. Energy 31, 2198–2206 (2006) [Google Scholar]
- F. Spertino, J. Ahmad, A. Ciocia, P. Di Leo, A.F. Murtaza, M. Chiaberge, Capacitor charging method for I-V curve tracer and MPPT in photovoltaic systems, Solar Energy 119 , 461–473 (2015) [CrossRef] [Google Scholar]
- Y. Erkaya, P. Moses, S. Marsillac, On-site characterization of PV modules using a portable, MOSFET based capacitive load, in 43rd IEEE Photovoltaic Specialist conference (2016) pp. 3119–3122 [Google Scholar]
- Zhikong et al., A capacitor based fast I–V characteristics I–V tester for photovoltaic arrays, Energy Proc. 145, 381–387 (2018) [CrossRef] [Google Scholar]
- Maxwell Technologies Supercapacitor Technical Note, link: http://www.afs.enea.it/project/oldprojects/protosphera/Proto-Sphera_Full_Documents/Messa_in_Opera_Multi-Pinch/Alimentazioni_con_SuperCapacitors/Alimentatore_Pinch/Maxwell/07%20UC%20vs%20Batteries.pdf. [Google Scholar]
- D.L. King, W.E. Boyson, J.A. Kratochvill, Photovoltaic Array Performance Model, Sandia Report, No: SAND2004-3535, 2004 [Google Scholar]
- AVX Supercapacitor, Available Online http://www.farnell.com/datasheets/2310575.pdf [Google Scholar]
- D.C. Montgomery, E.A. Peck, G. Geoffrey Vining, in Introduction to Linear Regression Analysis , 5th edn. (Willey Publishers, 2012) [Google Scholar]
- A. Louwen et al., Comprehensive characterization and analysis of PV module performance under real operating conditions, Prog. Photovolt. Res. Appl. 25 , 218–232 (2017) [CrossRef] [Google Scholar]
Cite this article as: Sudipta Basu Pal, Rahul Kumar, Konika Das Bhattacharya, Dipankar Mukherjee, Debkalyan Paul, Supercapacitor based PV measurement technique − quality assessment with poly-Si PV modules at IIEST, Kolkata, Int. J. Metrol. Qual. Eng. 10, 9 (2019)
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.